Occurrence of waterborne pathogens and antibiotic resistance in water supply systems in a small town in Mozambique
BMC Microbiology volume 22, Article number: 243 (2022)
. Microbiological quality of drinking water supplied in Moamba, a small town in southern Mozambique, was assessed by collecting and analyzing 91 water sample from 5 sampling sites: raw or inlet water, treated water and 3 household taps along the water distribution system. The presence of Escherichia coli as indicator fecal contamination, three bacterial pathogens, Vibrio cholerae, Salmonella and Campylobacter spp., and Cefotaximee resistant E. coli as antibiotic resistance determinant, was assessed.
. The results showed fecal contamination in all types of water samples: E. coli was found in 100% of inlet water samples, in 21% of treated water samples, and in 22% of tap water samples. No Salmonella spp. was detected during the study. The presence of V. cholerae was detected in 42% of all water samples tested: 100% of inlet water samples, in 16% of treated water samples, and in 23% household tap water samples. All V. cholerae confirmed isolates where genotyped by PCR as non-O1/non-O139; however, 9 isolates showed the presence of the genes encoding for cholera toxin. The presence of Campylobacter spp. was detected in 36% of the water samples tested: in 95% of inlet water samples, in 10% of treated water samples and in 23% household tap water samples. Cefotaxime resistant E. coli was detected in 63% of inlet water, 16% of treated water, and in 9% of tap water samples, these isolates were also resistant to multiple other antibiotics: ampicillin, streptomycin, tetracycline chloramphenicol. All 70 V. cholerae non-O1/non-O139 confirmed isolated were resistant to ampicillin, 51% to streptomycin, 13% to gentamycin, and 1 isolate was resistant to tetracycline; 13% showed a multi-drug resistant profile, being resistant to at least three antibiotics.
. The presence of fecal contamination and pathogens in the water treatment system and household taps in Moamba indicates a health risk for the population. This burden increases by the presence of bacterial pathogens showing multidrug resistance.
Universal access to water, the source of life for every human being and for the survival of the planet, has been recognized as a universal human right . Several pathogens such as enteric bacteria, viruses and parasites, are transmitted through consumption or exposure to contaminated water and cause major diseases that represent a global public health problem, particularly for children under the age of five [2, 3]. Despite growing efforts to ensure access to safe water, an estimated 20 million citizens will be exposed to contaminated water by 2030, and waterborne infections and epidemics continue to be a major global public health concern . Contaminated water represents also a possible route of human exposure to antibiotic resistant pathogens of environmental origin . Antibiotic resistance is increasingly a global public health concern leading to millions of deaths due to drug-resistant infection every year, with 700.000 deaths related to antimicrobial resistance are recorded annually . It is estimated that antimicrobial resistant infections may become the leading cause of death globally by 2050 with more than 300 millions (4.500.000 only in Africa) premature deaths expected because of drug resistance .
Sub-Saharan Africa is the area most at risk among the Sustainable Development Goals (SDG) regions . Several countries in this region rely on intermittent water supply (IWS), which provide piped water to consumers for less than 24 h per day. The risk of waterborne diseases due to microbial contamination of water in IWS is often high due to the ingress of pathogens in non or low-pressurized pipes through intrusion, back flow, release of particulates, or sloughing of biofilms [7, 8]. Furthermore, the reduced availability of piped water associated with IWS forces households to store water and/or the use alternative unsafe water sources, practices that increase the exposure to contaminated water [9,10,11].
In order to reduce waterborne diseases, an adequate assessment of the presence of pathogens is essential to implement appropriate water treatment practices [4, 12, 13]. However, there are no universal methods of detection and identification of waterborne pathogens that are applicable to different socio-economic contexts, which makes it difficult to obtain comparable measures and formulate appropriate policies [14, 15]. Current standard methods for monitoring microbial water quality are based on the detection of fecal indicator bacteria (FIBs), such as Escherichia coli or Enterococcus faecalis, the presence of which indicates fecal contamination of water . However, an inconsistent relationships between FIB and enteric pathogens occurrence in drinking water have been reported in different settings worldwide . Consumption of water free from FIBs have been associated with diarrheal disease outbreaks, likely due to treatment processes that are unable to completely eliminate the pathogens [18, 19]. Moreover, detection of pathogens in water is not part of routine water quality monitoring, and is restricted to research studies or in case of suspected outbreaks .
In Mozambique, information on waterborne diseases infections is relatively scarce but confirms that diarrheal diseases are a significant contributor to morbidity and mortality, especially among young children (8–10%) [20,21,22]. Enteric infections are predominatly caused by Rotavirus [23, pathogenic E. coli [24,25,26,27Salmonella [28, 29Campylobacter [30, and Vibrio cholerae [31,32,33]. The latter continue to represent a major public health burden as Mozambique continues on experiencing recurrent annual outbreaks of cholera in different parts of the country, caused by multi-drug resistant (MDR) V. cholerae, with incidences ranging from 0 to 211 per 100,000 population and periodically high case-fatality ratios [34,35,36]. However, little information is available on the contamination of raw and stored waters, mostly limited to the detection of FIB, with few studies detected the presence of waterborne pathogens by molecular methods [37, 38].
In Mozambique, water supply in small towns, where 15% of the country population resides [39, relies on IWS and it is characterized by high levels of leakage, limited hydraulic capacity and short water supply duration (< 12 h) . Van den Berg et al.  investigated the effects of operational strategies, such as increased disinfectant dosage, increased supply duration and first-flush, on drinking water quality in an IWS system in a small town of Mozambique. It demonstrated that water in distribution chain is fecally contaminated (E. coli indicator).
The aim of this study was to deepen the work conducted by van den Berg et al.  by investigating the presence of waterborne pathogens and antimicrobial pathogens in an IWS system in a small town of Mozambique. Standard cultivation methods were coupled with molecular techniques for the detection of E. coli as FIB, Extended Spectrum Beta Lactamase E. coli (Cefotaxime resistant E. coli) as indicator of antimicrobial resistance, and waterborne pathogens: Vibrio cholerae, Salmonella spp. and Campylobacter spp., and their antibiotic resistance profile. The results of this study are relevant for water operators, policy makers and researchers.
E. coli was detected in all sample types: in 100% of inlet water (I), in 21% of treated water samples (T0), and in 22% of tap water samples (T1, T2 and T3). E. coli counts for I ranged between 26 and 500 CFU/100 mL, with a mean of 185 CFU/100 mL. T0 showed fecal contamination only in May (133 CFU/100 mL), August (37 CFU/100 mL) of 2018 and May 2019 (20 CFU/mL) (Table 1).
The T1 tap sampling point showed E. coli in 3 out of 19 samples with counts less than 10 per 100 mL. At tap T2 E. coli was detected in 5 out of 18 samples with E. coli concentrations ranging between 11 and 100 CFU/100 mL in August 2018 and June 2019, respectively. In water collected at T3 E. coli was detected in 4 out of 16 samples, with concentrations ranging between 6 and 69 CFU/100 mL. In May 2018, all five locations were positive for E. coli and/or Cefotaxime resistant E. coli (Table 1).
Cefotaxime resistant E. coli
Cefotaxime resistant E. coli counts were reported in all sample’s types: in 63% (I), 16% (T0), and 9% (T1, T2 and T3). Counts for I ranged between 1 and 216 CFU/100 mL, with a mean of 14 CFU/100 mL (Table 1). Presence of Cefotaxime resistant E. coli was confirmed in treated water T0 in May (76 CFU/100 mL), August (1 CFU/100 mL) and November (11 CFU/100mL) of 2018. As for the taps, counts were positive for T1 only in May 2018 (29 CFU/100mL), for T2 in 3 out of 18 samples with concentrations ranging between 3 and 31 CFU/100 mL in May, August 2018 and June 2019, and for T3 in May 2018 (5 CFU/100 mL) (Table 1). Overall a significant correlation with the indicator in water samples was observed (r = 0.6, p-value = 3.945e-10). In May 2018, counts were high for all sample’s types except for T1 water where Cefotaxime resistant E. coli was detected but not the indicator (Table 1).
V. cholerae was detected in 42% of all water samples tested: 100% (I), 11% (T0), and in 23% (T1, T2 and T3) (Table 1). All V. cholerae confirmed isolates where genotyped as non-O1/non-O139 by PCR. In four inlet water samples from September through December 2018 and August 2019 V. cholerae non-O1/non-O139 was isolated with the genetic potential of producing cholera toxin (ctx+). All other V. cholerae non-O1/non-O139 isolates were CTX negative.
Salmonella spp. was not detected in any of the samples.
Campylobacter spp was detected in 36% of the water samples tested (n = 29): 95% (I), 10% (T0) on February and April 2019, and 23% (T1, T2 and T3) on April 2018, from August 2018 through May 2019 and in August 2019 (Table 1).
Selected Cefotaxime resistant E. coli confirmed isolates were tested for susceptibility to 12 antibiotics. All 15 strains tested showed resistance to multiple antibiotics. As expected all isolates were resistant to Cefotaxime, all were also resistant to ampicillin. Additionally, 10 isolates were resistant to streptomycin, 7 to tetracycline and 1 isolate was also resistant to chloramphenicol (Table 2). Isolates resistant to at least one other antibiotic were detected in all types of water samples tested. Ten isolates (62%) showed a MDR profile, being resistant to at least three antibiotics, five of these were isolated from I, two from T0, one from T1 and two from T2.
All 70 V. cholerae non-O1/non-O139 confirmed isolated were tested for susceptibility to 11 antibiotics. Of these, 69 isolates were resistant to ampicillin, 35 (51%) were resistant to streptomycin, 9 (13%) were resistant to gentamycin, and 1 isolate was resistant to tetracycline (Table 2). Nine isolates (13%) showed a MDR profile, being resistant to at least three antibiotics, and of these 5 isolates originated from I, 2 from T1 and 1 from each T1 and T3.
Free chlorine levels varied greatly among sample type. The highest mean value of chlorine was 1.2 mg/L detected at the outlet of the WTP (Fig. 1, Supplementary Table 4). Free chlorine levels at T0 ranged between 0.3 and 2.6 mg/L. In household tap water the level of free chlorine ranged between 0.1 mg/L at T1 in April 2019 to 2.3 mg/L at T2 in April 2018. T1 household water had the lowest mean values of free chlorine (Fig. 1, Supplementary Table 4). In 7% of all the samples taken at household taps (n = 44) free chlorine was less than 0.2 mg/L, in 57% had values comprised between 0.2 and 1 mg/L, and in 36% of the samples the free chlorine exceeded 1 mg/L (Fig. 1, Supplementary Table 4). Differences observed between free chlorine values detected at T1 and T0, T2 and T3 were significant at the 95% interval (p < 0.05).
Turbidity of the Inlet water ranged between 0.5 and 12.3 NTU (Fig. 2, Supplementary Table 4). For T0 water turbidity ranged between 0.1 and 10.3 NTU. Turbidity values recorded at household taps ranged from a minimum of 0.8 NTU to a maximum of 22.7 NTU. 93% of the total number of tap water samples (n = 44) analyzed were greater than 1.0 NTU of which 45% did not comply with the national standards of 5.0 NTU. The highest turbidity level at tap was recorded in March 2018. Statistically, the differences observed were not significant at 95% interval (p < 0.05).
The average temperature of the water remained stable at around 23℃ at all sampling locations throughout the study period. The average pH of the water ranged between 8.1 and 8.3, values fell within the range of legal requirement for drinking water (pH 6.5–8.5). Conductivity of the treated and household tap water ranged between 298 µS/cm and 721 µS/cm, within the range of 50 − 2,000 as legal requirements, with average values above 500 µS/cm (Fig. 2, Supplementary Table 4).
During this study, the level of fecal contamination of the Inkomati river water (mean value of 185 CFU/100 mL) was lower than levels reported for surface water in the neighboring Limpopo Province in South Africa (mean values of 0.3 to 1.4 × 104 CFU/100 mL) [42, and lower than three rivers in Ecuador (128 to 1248 MPN/100 mL) . E. coli counts were in average higher in the dry season (April-October) than in the wet season (November-March) indicating that lower level of river water affects the concentration of microbes.
When considering the removal of fecal contamination at the Moamba WTP, we recorded complete removal of E. coli in 79% of the samples. Samples showing E. coli contamination were collected in April, May and August of 2018 and June of 2019, and showed 2.62, 0.09, 0.16 and 0.33 log10 removal, respectively. In 95% of tap water samples the turbidity was greater than WHO level (1.0 NTU) to guarantee an effective disinfection process  (WHO 2017). High turbidity in filtered water is associated with poor removal of pathogens, sloughing of biofilms and ingress of contaminants through broken pipes .
Removal efficiency of fecal contamination did not correlate significantly with any of the physico-chemical parameters assessed. Our findings reported re-contamination during distribution at all three household taps, where 23% of water samples exceeded national standards for potable water parameters for E. coli. Fecal contamination monitoring of a IWS system in India reported 32% of samples exceeding WHO drinking water quality guidelines . Water collected from household taps was generally free of E. coli contamination as 77% of the samples consisted of non-detects. Prevalence of household tap samples contaminated with E. coli were 16%, 28% and 25% for Cimento, Matadouro and Bairro Sul, respectively. These values are in line with those reported in another study conducted on the same WTP . Similar values of E. coli contamination were reported in Maputo tap water (23% of samples) . Also, the prevalence of fecal contamination observed in our study reflects the variability observed in other IWS distribution networks [7, 8, 44].
Limitations of the fecal indicator paradigm have long been reported with the inconsistent relationships between FIB occurrence, enteric pathogens, and associated health risks [45,46,47,48]. The absence of E. coli does not eliminate the risk of the water being contaminated by enteric pathogens that may show a higher resistance to disinfection and the ability to persist in the distribution network in biofilms [4, 7]. In our study we have detected the presence of pathogens such as Vibrio cholerae and Campylobacter throughout the water supply in Moamba even when E. coli was not detected. 11% of the treated water samples were positive for V. cholerae and Campylobacter, while the two pathogens were detected in 18% and 15% of tap water samples, respectively, in absence of E. coli. V. cholerae survives better in estuarine waters than E. coli resulting in poor correlation of V. cholerae levels with fecal coliform concentrations in estuarine waters . Also, V. cholerae non-O1 is a natural inhabitant of waters and therefore it may have a greater fitness in water than the enteric commensal E. coli. In a recent study monitoring treated water quality, V. cholerae abundance was higher compared to E. coli after three days . The extended survival of V. cholerae in treated water may have serious public health implications.
V. cholerae non-O1/non-O139 was present in 74% of samples from Inkomati river. This pathogen has been widely reported in surface water in Mozambique and worldwide [51,52,53]. Nine V. cholerae non-O1/non-O139 isolates were positive for the presence of the ctxAB genes encoding the cholera toxin, the virulence factor causing the severe diarrhea associated with cholera disease. These isolates originated from inlet (5), treated water (1) and tap water (3) samples. Although rare in the environment, the detection of ctx genetic determinant in V. cholerae non-O1/non-O139 has been reported in several countries [54, 55, including Mozambique . The presence of this microorganism has been linked to cases of diarrheal diseases, representing a risk for the population consuming the water .
Detection of Campylobacter in 10% of treated water samples and in 19% household tap water samples further suggested environmental contamination and persistence of pathogens along the Moamba WTS distribution network. The contamination of water by Campylobacter can be linked to the presence of a major hatchery and the widespread smallholder family poultry producers in Moamba district .
Campylobacter detection did not correlate with the occurrence of E. coli as indicator of faecal contamination in treated and household tap water samples. In other studies the presence of Campylobacter spp. showed a lower correlation with fecal indicators respect to other pathogens such as Cryptosporidium/Giardia, pathogenic E. coli, and Salmonella spp .
Antibiotic resistant bacteria have been increasingly reported globally, not only restricted to clinical settings but also recovered from environmental samples, especially water. The pandemic diffusion of ESBL-producing Gram-negative bacteria in drinking water distribution systems is a major health concern, affecting mostly low-income countries in Asia and Africa [38, 60,61,62,63]. In our study, cefotaxime resistant E. coli, and V. cholerae strains resistant to several class of antibiotics were detected in inlet, treated and household water samples. The high prevalence (62%) of MDR E. coli, indicated that different classes of antibiotics are being co-selected with β-lactam resistance in the aquatic environment. A much lower incidence (10.7%) of ESBL E. coli was reported in tap water of Maputo . Also, 13% of V. cholerae non-O1/O139 isolates showed a MDR profile. Our results confirmed the rapid dissemination of AMR in environments that are not directly affected from major clinical inference, implying an overuse and misuse of antibiotics in local communities .
From our finding we can conclude that the detection and monitoring of major microbial pathogens at different points of the drinking water treatment process and distribution network is crucial for water quality management, especially in IWS where non- or low pressurized pipes permit re-contamination of treated water. A contaminated water distribution system may act as source of waterborne pathogens and a mean for spreading them between communities. On the other hand, in settings like the ones surveyed in our study where low level of sanitation and hygiene allow for circulation of FIB and pathogens between humans, animals and household environment, measurement of standard tap drinking water quality alone may not be sufficient to accurately predict the safety and health implications associate with its consumption. New practices are needed to support monitoring approaches that go beyond the routine measurement of E. coli or FIB as mean to assess drinking water quality.
This study was conducted in Moamba, a town located in the southern Maputo province of Mozambique. Moamba District has an area of 4,628 square km, and the town has a population of 24,650 inhabitants . Since 2013 the town is supplied by an IWS system with the capacity of 3,000 m³/day. The source for the production of drinking water is the Incomáti river. Water is abstracted 3.5 km from the water treatment plant (WTP) and subjected to coagulation-flocculation based on dosing of aluminium sulphate, rapid sand filtration by six pressure filters with a capacity of 40 m³/hour each, and disinfection by dosing chlorine solution with a calculated dose of 1.8 mg Cl2/L41.
The system supplies water to all but three neighborhoods of Moamba, reaching 83% of the population through a distribution network with a total length of 45 km with approximately 3,336 connections. The WTP is operates in two cycles (morning and afternoon) and disinfected water is stored in a 500 m  reservoir and 150 m  water tower before being distributed via the network .
Samples were collected from the intake source water for drinking water production (inlet, I), treated water at WTP (outlet, T0), drinking water from 3 taps in different neighborhoods of Moamba: Cimento (T1), Matadouro (T2) and Barrio Sul (T3). Sampling locations had a piping distance from the WTP of 800 m, 2,200 m and 1,863 m for T1, T2 and T3, respectively (Fig. 1).
Nineteen sampling rounds were carried out on a monthly basis between March 2018 and October 2019 during both the dry (April 2018 - October 2018 and April 2019 - September 2019) and wet seasons (March 2018 and November 2018 - March 2019). A total of 91 water samples were collected at the 5 sampling sites. For sampling trips in March and April 2019 it was not possible to collect water from household T3, and in April 2019 it was not possible to collect water from households T2 and T3, because residents reported lack of water at these sites.
Water samples collection
Water samples were collected in the morning supply cycle, between 10 and 11 AM. For microbiological and physico-chemical analyses, 500 mL water samples were aseptically collected in sterile collection bottles previously cleaned with detergent and sterilized by autoclaving for 20 min at 121 °C prior to use. Collection bottles were supplemented with thiosulfate tablets (Starplex Scientific Inc, USA) to inactivate available chlorine.
Water samples of inlet and outlet of the WTP and tap water were collected after flushing the water for 2 min and kept in a cooler during transport to Center for Biotechnology laboratory for analysis. Samples were processed on the same day, typically within 2–4 h of collection.
Enumeration of E. coli and cefotaxime resistant E. coli as well as detection of the pathogens Vibrio cholerae, Salmonella spp. and Campylobacter spp. was carried out in all water samples (I, T0, T1, T2, T3) by testing different volumes per parameters and per sample location (Supplementary Table 1).
Volumes ranging between 10 mL to 100 mL were filtered through a 0.47 μm polycarbonate membrane and incubated in plates or 50 mL of enrichment selective media. Volumes of 0.1 mL and 1 mL were either added to sterile PBS and filtered or added directly to 10 and 9 mL of specific enrichment selective media, respectively (Supplementary Table 1).
Enumeration of total E. coli was done according to ISO 9308-1 standard method. Different volumes (Supplementary Table 1) were filtered and membranes were placed on Tryptone Bile X-glucuronide (TBX) (Merck KGaA, USA) plates and incubated overnight at 35–37 °C. After incubation, plates were checked for growth and presumptive E. coli β-glucuronidase-positive (blue/green) colonies in each plate containing less than 300 were counted as colony forming units (CFU).
Cefotaxime resistant E. coli
Different volumes (Supplementary Table 1) were filtered and membranes were placed onto TBX plates supplemented with cefotaxime (CTX) (4ug/mL) and incubated overnight at 35–37 °C. After incubation, plates were checked for growth and presumptive E. coli β-glucuronidase-positive (blue/green) colonies in each plate containing less than 300 were counted as CFU. At least 5 colonies were picked and stored in glycerol at -80℃ for species confirmation by PCR and antibiotic resistance profile.
V. cholerae was detected as described by Huq et al. . After filtration, membranes were incubated in Alkaline Peptone Water (APW). The enrichment broth was incubated overnight at 35–37 °C, followed by plating onto thiosulfate citrate bile salt sucrose (TCBS) agar (BD, USA) and overnight incubation at 35–37 °C. Plates were checked for growth of presumptive V. cholerae (yellow, with a diameter of 2–3 mm) and at least 5 presumptive V. cholerae colonies were picked, plated onto Luria Bertani (LB) agar, incubated over night at 35–37 °C and then stored in glycerol at -80℃ for molecular analysis and antibiotic susceptibility.
Salmonella spp. detection was carried out according to the ISO 19,250 standard method. Membranes were transferred to Buffered Peptone Water for non-selective enrichment during overnight incubation at 35–37 °C. The following day 0.1 mL of enrichment was added to 10 mL of Rappaport-Vassiliadis soya peptone broth for selective enrichment for 24 h at 41.5 °C. Samples exhibiting growth were plated onto Xylose Lysine Deoxycholate (XLD) agar and incubated 24 h at 35–37 °C. Tubes not exhibiting growth were re-incubated for 24 h at 35–37 °C and then checked for exhibiting growth. XLD plates were checked for growth and presumptive Salmonella colonies were subcultured onto Brilliant Green (BG) agar plates and incubated for 24 h at 35–37 °C for further confirmation. At least 5 presumptive Salmonella (pink-red on BG) colonies were stored in glycerol at -80℃ for molecular analysis for confirmation and antibiotic resistance profile.
For Campylobacter spp. detection Preston Broth was used for enrichment after filtration and incubated 48 h at 35–37 °C in microaerophilic conditions. Tubes exhibiting growth were plated onto Karmali agar and incubated 48 h at 35–37 °C in microaerophilic conditions. Karmali plates were checked for growth and five presumptive Campylobacter spp colonies were stored in glycerol at -80℃ for molecular analysis.
Molecular analysis: species confirmation and typing
DNA was isolated from the cells by the boiling method. Isolates were retrieved from glycerol stocks by plating onto specific media (see above) and incubated over night at 37 °C. From each isolate, one colony was picked and added to 500 µL of sterile PCR grade water and incubated 10 min at 95 °C and the boiled cells immediately transferred onto ice for 15 min. Tubes were then centrifuged at 13,000 rpm for 10 min and 400 µl of supernatant was transferred in a clean sterile tube and 3 µL was used as template for PCR.
Species confirmation and typing of the isolates was done by PCR, by using selected primers as shown in Supplementary Table 2. Vibrio cholerae was confirmed by PCR based on the ompW gene encoding for the outer membrane protein . A multiplex PCR was performed to check if the isolates were V. cholerae O1 or O139 and if the isolates possessed the genetic potential of producing cholera toxin . Campylobacter jejuni in the isolated Campylobacter colonies was confirmed by a PCR assay based on the presence of the gene hsp60 encoding the heat stable protein as described by Park et al. . Salmonella suspected colonies were tested by a PCR as described by Martinez-Ballesteros et al. . A PCR assay was performed as to confirm E. coli based on 16 S and uidA gene .
Antibiotic resistance profile
Selected cefotaxime resistant E. coli and V. cholerae isolates were tested for their antimicrobial susceptibilities by replica plating onto Mueller Hinton agar supplemented with antibiotic at breakpoint concentrations (Supplementary Table 3)72. The minimal inhibitory concentrations (MIC) considered to represent resistance to a given antibiotic were those determined by CLSI72. Isolates with intermediate susceptibility were categorized as being susceptible.
Physico-chemical water quality parameters were measured on site. Conductivity and pH were measured using a PT157 (Palintest, United Kingdom) probe, and temperature was recorded using a PT155 (Palintest, United Kingdom) probe. The Palintest Turbimeter Plus PTH092 was used to analyse the turbidity of the samples. The Palintest Photometer 7100 PTH7100 was used to analyse free and total chlorine. Meters were calibrated on a monthly basis.
Concentrations of E. coli (CFU/100 mL) and physico-chemical parameters were logarithmically (base 10) transformed. For E. coli, removal was calculated as the difference between the concentrations obtained in the raw water (I) and the concentrations obtained in the treated water (T0). The normality distribution of E. coli concentrations and physical-chemical parameters data was checked by Shapiro-Wilk’s test and data analysis and plots were performed using R Studio software V. 1.4.1103. The correlations among different parameters using Spearman’s correlation test. Spearman’s coefficient (r) with P values < 0.05 were considered statistically significant.
All data is available in the manuscript and in the supporting material.
UN. The human right to water and sanitation. Resolution adopted by the General Assembly on 28 July 2010. https://digitallibrary.un.org/record/687002?ln=en.
WHO/UNICEF JMP. Progress on household drinking water, sanitation and hygiene 2000–2017. Special focus on inequalities. New York: United Nations Children’s Fund (UNICEF) and World Health Organization (WHO); 2019.
Prüss-Ustün A, Wolf J, Bartram J, Clasen T, Cumming O, Freeman MC, Gordon B, Hunter PR, Medlicott K, Johnston R. Burden of disease from inadequate water, sanitation and hygiene for selected adverse health outcomes: An updated analysis with a focus on low- and middle-income countries. Int J Hyg Environ Health. 2019. doi:https://doi.org/10.1016/j.ijheh.2019.05.004.
Holcomb DA, Stewart JR. Microbial Indicators of Fecal Pollution: Recent Progress and Challenges in Assessing Water Quality. Curr Environ Health Rep. 2020. https://doi.org/10.1007/s40572-020-00278-1.
Iwu CD, du Plessis E, Korsten L, Okoh AI. Antibiogram imprints of E. coli O157: H7 recovered from irrigation water and agricultural soil samples collected from two district municipalities in South Africa. Int J Environ Stud. 2021 Nov;78(6)(2):940–53.
UN Environmental Dimensions of Antimicrobial Resistance Summary for Policymakers. 2022. https://www.unep.org/resources/report/summary-policymakers-environmental-dimensions-antimicrobial-resistance.
Kumpel E. and Kara L. Nelson. Mechanisms Affecting Water Quality in an Intermittent Piped Water Supply. Environ Sci Technol. 2014. https://doi.org/10.1021/es405054u.
Bivins AW, Sumner T, Kumpel E, Howard G, Cumming O, Ross I, Nelson K, and Joe Brown. 2017. Estimating Infection Risks and the Global Burden of Diarrheal Disease Attributable to Intermittent Water Supply Using QMRA. Environmental Science & Technology. 2017; https://doi.org/10.1021/acs.est.7b01014.
Agathokleous A, Christodoulou S. The impact of intermittent water supply policies on urban water distribution networks. Procedia engineering. 2016 Jan 1;162:204 – 11.
Galaitsi SE, Russell R, Bishara A, Durant JL, Bogle J, Huber-Lee A. Intermittent domestic water supply: A critical review and analysis of causal-consequential pathways. Water. 2016 Jun 30;8(7):274.
Klingel P. Technical causes and impacts of intermittent water distribution. Water Sci Technology: Water Supply. 2012 Jul;12(4):504–12.
Peletz R, Kumpel E, Bonham M, Rahman Z, Khush R. To what extent is drinking water tested in sub-Saharan Africa? A comparative analysis of regulated water quality monitoring. Int J Environ Res Public Health. 2016 Mar;13(3):275.
Kumar S, Anwer R, Sehrawat A, Yadav M, Sehrawat N. Assessment of Bacterial Pathogens in Drinking Water: a Serious Safety Concern. Current Pharmacology Reports. 2021 Oct;7(5):206 – 12.Straub TM, Chandler DP. Towards a unified system for detecting waterborne pathogens. J. Microbiol. Methods. 2003; https://doi.org/10.1016/S0167-7012(03)00023-X.
Bridle H, editor. Waterborne pathogens: detection methods and applications. Academic Press; 2020. Oct 6.
Cotruvo JA. 2017 WHO guidelines for drinking water quality: first addendum to the fourth edition. Journal-American Water Works Association. 2017 Jul;109(7):44–51.
LeChevallier MW, Au KK. Water treatment and pathogen control. Iwa Publishing; 2004. Aug 31.
Figueras MJ, Borrego JJ. New perspectives in monitoring drinking water microbial quality. Int J Environ Res public health. 2010 Dec;7(12):4179–202.
Saxena G, Bharagava RN, Kaithwas G, Raj A. Microbial indicators, pathogens and methods for their monitoring in water environment. J Water Health. 2015 Jun;13(2):319–39.
Nhampossa T, Mandomando I, Acacio S, Quintó L, Vubil D, Ruiz J, Nhalungo D, Sacoor C, Nhabanga A, Nhacolo A, Aide P. Diarrheal disease in rural Mozambique: Burden, risk factors and etiology of diarrheal disease among children aged 0–59 months seeking care at health facilities. PloS one. 2015 May 14;10(5):e0119824.
Chissaque A, de Deus N, Vubil D, Mandomando I. The epidemiology of diarrhea in children under 5 years of age in Mozambique. Curr Trop Med Rep. 2018 Sep;5(3):115–24.
Raza O, Mansournia MA, Foroushani AR, Holakouie-Naieni K. Exploring spatial dependencies in the prevalence of childhood diarrhea in Mozambique using global and local measures of spatial autocorrelation. Med J Islamic Repub Iran. 2020;34:59.
Deus ND, João E, Cuamba A, Cassocera M, Luís L, Acácio S, Mandomando I, Augusto O, Page N. Epidemiology of rotavirus infection in children from a rural and urban area, in Maputo, southern Mozambique, before vaccine introduction. J Trop Pediatr. 2018 Apr;64(2):141–5.
Sumbana J, Taviani E, Manjate A, Paglietti B, Santona A, Colombo MM. Genetic determinants of pathogenicity of Escherichia coli isolated from children with acute diarrhea in Maputo, Mozambique. The Journal of Infection in Developing Countries. 2015 Jul 4;9(06):661-4.
Mandomando I, Vubil D, Boisen N, Quintó L, Ruiz J, Sigaúque B, Nhampossa T, Garrine M, Massora S, Aide P, Nhacolo A. Escherichia coli ST131 clones harbouring AggR and AAF/V fimbriae causing bacteremia in Mozambican children: Emergence of new variant of fimH27 subclone. PLoS neglected tropical diseases. 2020 May 1;14(5):e0008274.
Sumbana JJ, Santona A, Fiamma M, Taviani E, Deligios M, Zimba T, Lucas G, Sacarlal J, Rubino S, Paglietti B. Extraintestinal pathogenic Escherichia coli ST405 isolate coharboring blaNDM-5 and blaCTXM-15: a new threat in Mozambique. Microbial Drug Resistance. 2021 Dec 1;27(12):1633-40.
Manhique-Coutinho L, Chiani P, Michelacci V, Taviani E, Bauhofer AF, Chissaque A, Cossa-Moiane I, Sambo J, Chilaúle J, Guimarães EL, Salência J. Molecular characterization of diarrheagenic Escherichia coli isolates from children with diarrhea: A cross-sectional study in four provinces of Mozambique: Diarrheagenic Escherichia coli in Mozambique. International Journal of Infectious Diseases. 2022 Aug 1;121:190-4.
Mandomando I, Bassat Q, Sigaúque B, Massora S, Quintó L, Ácacio S, Nhampossa T, Vubil D, Garrine M, Macete E, Aide P. Invasive Salmonella infections among children from rural Mozambique, 2001–2014. Clinical Infectious Diseases. 2015 Nov 1;61(suppl_4):S339-45.
García V, Mandomando I, Ruiz J, Herrera-León S, Alonso PL, Rodicio MR. Salmonella enterica serovars Typhimurium and Enteritidis causing mixed infections in febrile children in Mozambique. Infect Drug Resist. 2018;11:195.
Knee J, Sumner T, Adriano Z, Berendes D, de Bruijn E, Schmidt WP, Nalá R, Cumming O, Brown J. Risk factors for childhood enteric infection in urban Maputo, Mozambique: A cross-sectional study. PLoS neglected tropical diseases. 2018 Nov 12;12(11):e0006956.
Ansaruzzaman M, Bhuiyan NA, Nair GB, Sack DA, Lucas M, Deen JL, Ampuero J, Chaignat CL. Mozambique Cholera Vaccine Demonstration Project Coordination Group. Cholera in Mozambique, variant of Vibrio cholerae. Emerging infectious diseases. 2004 Nov;10(11):2057.
Mandomando I, Espasa M, Vallès X, Sacarlal J, Sigaúque B, Ruiz J, Alonso P. Antimicrobial resistance of Vibrio cholerae O1 serotype Ogawa isolated in Manhica District Hospital, southern Mozambique. Journal of antimicrobial chemotherapy. 2007 Sep 1;60(3):662-4.
Langa JP, Sema C, De Deus N, Colombo MM, Taviani E. Epidemic waves of cholera in the last two decades in Mozambique. The Journal of Infection in Developing Countries. 2015 Jul 4;9(06):635 – 41.
Dengo-Baloi LC, Semá-Baltazar CA, Manhique LV, Chitio JE, Inguane DL, Langa JP. Antibiotics resistance in El Tor Vibrio cholerae 01 isolated during cholera outbreaks in Mozambique from 2012 to 2015. PloS one. 2017 Aug 8;12(8):e0181496.
Semá Baltazar C, Langa JP, Dengo Baloi L, Wood R, Ouedraogo I, Njanpop-Lafourcade BM, Inguane D, Elias Chitio J, Mhlanga T, Gujral L, Gessner D. B. Multi-site cholera surveillance within the African Cholera Surveillance Network shows endemicity in Mozambique, 2011–2015. PLoS neglected tropical diseases. 2017 Oct 9;11(10):e0005941.
Cambaza E, Mongo E, Anapakala E, Nhambire R, Singo J, Machava E. Outbreak of cholera due to cyclone Kenneth in northern Mozambique, 2019. Int J Environ Res Public Health. 2019 Aug;16(16):2925.
Taviani E, Ceccarelli D, Lazaro N, Bani S, Cappuccinelli P, Colwell RR, Colombo MM. Environmental Vibrio spp., isolated in Mozambique, contain a polymorphic group of integrative conjugative elements and class 1 integrons. FEMS microbiology ecology. 2008 Apr 1;64(1):45–54.
Salamandane A, Vila-Boa F, Malfeito-Ferreira M, Brito L. High fecal contamination and high levels of antibiotic-resistant Enterobacteriaceae in water consumed in the city of Maputo, Mozambique. Biology. 2021 Jun 20;10(6):558.
Macario L. Mozambique-AFRICA EAST-P173518-Rural and Small Towns Water Security Project-Procurement Plan.
Gumbo B, Juizo D, Van der Zaag P. Information is a prerequisite for water demand management: experiences from four cities in Southern Africa. Physics and Chemistry of the Earth, Parts A/B/C. 2003 Jan 1;28(20–27):827 – 37.
van den Berg H, Quaye MN, Nguluve E, Schijven J, Ferrero G. Effect of operational strategies on microbial water quality in small scale intermittent water supply systems: The case of Moamba, Mozambique. Int J Hyg Environ Health. 2021; doi:0.1016/j.ijheh.2021.113794.
Mwabi J, Mamba B, Momba M. Removal of Waterborne Bacteria from Surface Water and Groundwater by Cost-Effective Household Water Treatment Systems (HWTS): A Sustainable Solution for Improving Water Quality in Rural Communities of Africa. Water SA. 2012. https://doi.org/10.4314/wsa.v39i4.2.
Rao G, Eisenberg JNS, Kleinbaum DG, Cevallos W, Gabriel Trueba, and Karen Levy. Spatial Variability of Escherichia Coli in Rivers of Northern Coastal Ecuador. Water. 2015; https://doi.org/10.3390/w7020818.
Shaheed A, Orgill J, Ratana C, Montgomery MA, Jeuland MA. and J. Brown. Water quality risks of ‘improved’ water sources: evidence from Cambodia. Tropical Med Int Health. 2014. https://doi.org/10.1111/tmi.12229.
Korajkic A, McMinn BR. and Valerie J. Harwood. Relationships between Microbial Indicators and Pathogens in Recreational Water Settings. Int J Environ Res Public Health. 2018. https://doi.org/10.3390/ijerph15122842.
Kelly ER, Cronk R, Kumpel E, Howard G, Bartram J. How We Assess Water Safety: A Critical Review of Sanitary Inspection and Water Quality Analysis. Sci Total Environ. 2020; https://doi.org/10.1016/j.scitotenv.2020.137237.
Charles KJ, Nowicki S, Jamie K. Bartram. A Framework for Monitoring the Safety of Water Services: From Measurements to Security. Npj Clean Water. 2020. https://doi.org/10.1038/s41545-020-00083-1.
Nowicki S, deLaurent ZR, Etienne P, de Villiers G, Githinji, Katrina J. Charles. The Utility of Escherichia Coli as a Contamination Indicator for Rural Drinking Water: Evidence from Whole Genome Sequencing. PLoS ONE. 2021. https://doi.org/10.1371/journal.pone.0245910.
Colwell RR, Huq A. Vibrios in the environment: viable but nonculturable Vibrio cholerae. Vibrio cholerae and cholera: molecular to global perspectives. 1994 Mar 10:117–33.
Djaouda M, Wadoubé Z, Baponwa O, et al. Survival and growth of Vibrio cholerae and Escherichia coli in treated groundwater consumed in northern Cameroon. Appl Water Sci. 2020. https://doi.org/10.1007/s13201-020-01328-7.
Taviani E, Ceccarelli D, Lazaro N, Bani S, Cappuccinelli P, Colwell RR. and Mauro M. Colombo. Environmental Vibrio Spp., Isolated in Mozambique, Contain a Polymorphic Group of Integrative Conjugative Elements and Class 1 Integrons: ICEs and Integrons in Environmental Mozambican Vibrio. FEMS Microbiol Ecol. 2008. https://doi.org/10.1111/j.1574-6941.2008.00455.x.
Hasan NA, Ceccarelli D, Grim CJ, Taviani E, Choi J, Sadique A, Alam M, Siddique AK, Sack RB, Huq A, Colwell RR. Distribution of virulence genes in clinical and environmental Vibrio cholerae strains in Bangladesh. Appl Environ Microbiol. 2013 Sep;15(18):5782–5. 79(.
Trindade LM da, Luiz Claudio Gomes Correa Filho, Denise Suellen Amorim de Sousa Santos, Nayara Rufino Sousa, Elivam Rodrigues Vale, Daniela Cristiane da Cruz Rocha, and Lena Líllian Canto de Sá Morais. Virulence Associated Factors in Bacteria from Water Bodies in Belem, Para, Brazil: Bacteriological Composition and Threat to Public Health.2021; https://doi.org/10.2166/washdev.2021.239.
Bhattacharya T, Chatterjee S, Maiti D, Bhadra RK, Takeda Y, Balakrish Nair G, Ranjan K. Nandy. Molecular Analysis of the RstR and OrfU Genes of the CTX Prophages Integrated in the Small Chromosomes of Environmental Vibrio Cholerae Non-O1, Non-O139 Strains. Environ Microbiol. 2006. https://doi.org/10.1111/j.1462-2920.2005.00932.x.
Biswas Q, Purohit A, Kumar A, Rakshit D, Maiti D, Das B, Bhadra RK. Genetic and mutational analysis of virulence traits and their modulation in an environmental toxigenic Vibrio cholerae non-O1/non-O139 strain, VCE232. Microbiology. 2022. https://doi.org/10.1099/mic.0.001135.
Colombo MM, Mastrandrea S, Santona A, de Andrade AP, Uzzau S, Rubino S, Cappuccinelli P. 1994. “Distribution of the Ace, Zot, and CtxA Foxin Genes in Clinical and Environmental Vibrio Cholerae. The Journal of Infectious Diseases. 1994;https://doi.org/10.1093/infdis/170.3.750.
Igere BE, Okoh AI, Nwodo UU. Non-serogroup O1/O139 agglutinable Vibrio cholerae: a phylogenetically and genealogically neglected yet emerging potential pathogen of clinical relevance. Arch Microbiol. 2022. https://doi.org/10.1007/s00203-022-02866-1.
FAO. 2013. Poultry Sector Mozambique. FAO Animal Production and Health Livestock Country Reviews. No. 5. Rome.
Korajkic A, McMinn BR. and Valerie J. Harwood. Relationships between Microbial Indicators and Pathogens in Recreational Water Settings. Int J Environ Res Public Health. 2018. https://doi.org/10.3390/ijerph15122842.
Tacão M, Moura A, Correia A, and Isabel Henriques. 2014. “Co-Resistance to Different Classes of Antibiotics among ESBL-Producers from Aquatic Systems.” Water Researc. 2014;https://doi.org/10.1016/j.watres.2013.09.021.
Mahmud ZH, Kabir MH, Ali S, Moniruzzaman M, Imran KM, Nafiz TN, Islam MS, Hussain A, Hakim SA, Worth M, Ahmed D. Extended-spectrum beta-lactamase-producing Escherichia coli in drinking water samples from a forcibly displaced, densely populated community setting in Bangladesh. Frontiers in public health. 2020 Jun 18;8:228.
Johnson A, Ginn O, Bivins A, Rocha-Melogno L, Tripathi SN, Brown J. Extended-spectrum beta-lactamase (ESBL)-positive Escherichia coli presence in urban aquatic environments in Kanpur, India. Journal of water and health. 2020 Oct 1;18(5):849 – 54.
Asaduzzaman M, Rousham E, Unicomb L, Islam MR, Amin MB, Rahman M, Hossain MI, Mahmud ZH, Szegner M, Wood P, Islam MA. Spatiotemporal distribution of antimicrobial resistant organisms in different water environments in urban and rural settings of Bangladesh. Sci Total Environ. 2022. https://doi.org/10.1016/j.scitotenv.2022.154890.
Iskandar K, Molinier L, Hallit S, Sartelli M, Catena F, Coccolini F, Hardcastle TC. Christine Roques, and Pascale Salameh. Drivers of Antibiotic Resistance Transmission in Low- and Middle-Income Countries from a ‘One Health’. Perspective—A Rev Antibiot. 2020. https://doi.org/10.3390/antibiotics9070372.
Anuário Estatístico. Instituto Nacional de Estatistica. 2018. http://www.ine.gov.mz.
Huq A, Haley BJ, Taviani E, Chen A, Hasan NA, Colwell RR. Detection, isolation, and identification of Vibrio cholerae from the environment. Curr protocols Microbiol. 2012 Aug;26(1):6A-5.
Nandi B, Nandy RK, Mukhopadhyay S, Nair GB, Shimada T, Ghose AC. Rapid method for species-specific identification of Vibrio cholerae using primers targeted to the gene of outer membrane protein OmpW. J Clin Microbiol. 2000; doi:0.1128/JCM.38.11.4145-4151.2000.
Hoshino K, Yamasaki S, Mukhopadhyay AK, Chakraborty S, Basu A, Bhattacharya SK, Nair GB, Shimada T, Takeda Y. Development and evaluation of a multiplex PCR assay for rapid detection of toxigenic Vibrio cholerae O1 and O139. 1998. FEMS Immunol Med Microbiol. Mar;20(3):201-7. doi: https://doi.org/10.1111/j.1574-695X.1998.tb01128.x. PMID: 9566491.
Park SH, Hanning I, Jarquin R, Moore P, Donoghue DJ, Donoghue AM, Ricke SC. 2011. Multiplex PCR assay for the detection and quantification of Campylobacter spp., Escherichia coli O157:H7, and Salmonella serotypes in water samples, FEMS Microbiology Letters. 2011; https://doi.org/10.1111/j.1574-6968.2010.02188.x.
Martinez-Ballesteros I, Paglietti B, Rementeria A, Laorden L, Garcia-RicobarazaM, Bikandi J, Rubino S, Garaizar J. Intra- and inter-laboratory evaluation of an improved multiplex-PCR method for detection and typing of Salmonella. J Infect Dev Ctries. 2012. doi:https://doi.org/10.3855/jidc.2445.
Bej AK, DiCesare JL, Haff L, Atlas RM. Detection of Escherichia coli and Shigella spp. in water by using the polymerase chain reaction and gene probes for uid. Appl Environ Microbiol. 1991;57:1013–7. https://doi.org/10.1128/aem.57.4.1013-1017.1991.
CLSI. Performance Standards for Antimicrobial Susceptibility Testing. 31st ed. Wayne: Clinical and Laboratory Standards Institute; 2021.
The WHO and the Advisory Group on Integrated Surveillance on AMR (AGISAR) provided the “Tricycle protocol” for ESBL detection. The authors are grateful to Pedro Cardoso of Collins Lda.
This study was funded by the Dutch Ministry of Foreign Affairs through the DGIS IHE Delft Programmatic Cooperation 2016–2020 (DUPC2) through project SMALL: water supply and sanitation in small towns. ET was supported by the Italian Agency for Cooperation Development through the BioForMoz AID12089 program.
Ethics approval and consent to participate
Consent for publication
The authors declare no conflict of interest.
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
Electronic supplementary material
Below is the link to the electronic supplementary material.
About this article
Cite this article
Taviani, E., van den Berg, H., Nhassengo, F. et al. Occurrence of waterborne pathogens and antibiotic resistance in water supply systems in a small town in Mozambique. BMC Microbiol 22, 243 (2022). https://doi.org/10.1186/s12866-022-02654-3